I’ve got several LW products throughout the house and recently installed a single gang dimmer in the lounge to control 11x 8w led downlights.
This initially worked fine but eventually failed – I’m assuming due to the load.
There is no way to split them into two rings without ripping down most of the ceiling etc which has just been plastered so my question is whether I have to accept that I’ll have to use a normal switch in that room or is there another way / product that will handle the load and still communicate with the hub / app / Alexa and be able to be used as part of events etc.
Thanks in advance!
You must be logged in to reply to this topic.